The new Zonescan leak noise logger is available from Gutermann .
How do Zonescan leak noise logger work?
Zonescan leak noise loggers are deployed throughout the water distribution network at regular intervals (often attached to valve spindles or fire hydrants via the integrated magnetic base).
The spacing between Zonescan leak noise loggers depends on the pipe material, typically 80 metres for PVC Pipes, 100 metres for AC and 130 metres for iron pipes.
The Zonescan leak noise loggers continuously monitor and analyse noise characteristics within the distribution system and can detect and identify the presence and location of a leak.
Once in range of a Zonescan leak noise logger, a patrol operator will receive automatic notification from the systems voice embedded host software, first identifying the unit, before announcing the presence or probability of a leak at that point in the water network.
If audible confirmation of the leak noise is desired, the operator can, at any time, listen directly to the digitally transmitted leak noise.
Logged results are displayed in the software database as a Project Table:
Each result is given as a Leak Value between 0 and 100 for initial interpretation. This Leak Value is determined by the level and occurrence of the logged decibel readings.
The operator sets the Leak Value threshold within the host software. This determines whether the result is indicated in red (caution, probable leak), orange (possible leak) or green (no leak). The same threshold is also used for triggering the audio warnings if required.
The Leak Value can be used to prioritise detection/confirmation tasks. For example, with the Leak Value threshold set to 30, quiet, low volume leakage (such as weeping fire hydrants and passing boundary valves) may still be highlighted in orange in the project table, along with greater volume leaks.
With the threshold set to 50, these lower volume/priority leaks will be coloured green in the Project Table and will not trigger a leak audio warning to the patrol engineer.
Because the patrol operator sets this threshold level based on his local knowledge of the network, different logged areas with different average pressures and pipe materials can be patrolled with improved effectiveness and efficiency.
The logged decibel values for each logger are displayed in the Measurements Graph.
Each Zonescan leak noise logger has a revolving memory that will retain 30 days of measurements graphs and 180 days of Leak Values, with old value being overwritten when the memory is full.
The storage of historic information is only limited by the host PC’s memory. An acoustic fingerprint can be built up and viewed in the Measurements window allowing a degree of local asset appraisal to be carried out.